Todays job of the month brings us to ilford in east london. The job entailed diagnostics of a leak into the clients bathroom. it was agreed that some investigative works should be carried out as there was no broken tiles or anything else visually that could be causing the issue. we stripped the tiles from the side of the dormer to check the soaker system as these can sometimes move or slip. we ruled out corrosion in this instance due to the age of there loft conversion. when we stripped the tiles it was found that no issue with the soakers in this instance. however there was a lot of debris build up behind the tiles which was causing the rainwater to back up and then find its way above the soaker system and then down the roof rafter and ingressing the property lower down the roof. we cleaned the debris and cut back the rotten batten prior to re instating the roof tiles. we also rearranged the shoe on the guttering to point slightly away from the side of the roof.
Our team done another great remedial fix and have guaranteed this for a period of one year with a insurance backed guarantee